TIPS FOR TROUBLE SHOOTING THE 4 BUTTON COMFORT CONTROL SYSTEMS
If you have one of my refurbished thermostats it has been
tested 100% for all functions for multiple zones, first after refurbishing and
then again just prior to shipping, So,
if you are having problems,- It is
something other than the thermostat so here are some things to check, (OR
– if your are having problems with your original thermostat)
If the thermostat will not activate -- There is usually no
12 Volts available at the thermostat. Check
the 3A fuse in the Control Board -- verify the RJ-11 (telephone type) connector
at the control board is plugged in firmly.
Take the thermostat off the wall and check for 12V on the terminals
behind the ON/OFF switch -- you must have 12V there on the center terminal with
switch OFF--- and on the Left terminal with the switch ON.
If you can not go to Zone 2 - (Zone change is done by
pressing the top 2 buttons and releasing at the same time) If
Zone 1 does not display (small “1”) and the Zone 2 DIP switch is ON, there is a
fault with the communication cable (Phone cable) from Zone 1 to Zone 2 and the
thermostat cannot detect Zone 2 which is necessary to show the zones on the display. Un-plug and re-plug the RJ-11 connectors to
wipe the contacts. If no change, run a
test cable from Z-1 to Z-2 with the thermostat connected to Z-1. If no change with test cable there is a fault
with Z-2 control board. The communication cable is different (parallel wired)
that a phone extension cable (series wired).
I can provide a communication test cable, with instructions, for $25.00
plus $5.00 shipping
If the Air Condition will not come on --
First select a fan speed and if the fan does not come on in about 6
seconds the possibilities are : a dead
spot or a bad fan motor (rotate the fan blade and try again) - be
sure 120 V is available on the Black wire in the junction box. --IF 120 volts available reset the breakers. If
120 V is available probably a faulty control board. After getting the fan to function, select
COOL and set a low temp. The compressor should
start in 2 to 3 minutes -- If not – possible bad compressor or faulty control
If Furnace will not display -- The Control Board must
receive 12 volts from the furnace on either one of the 2 blue wires at the
control board. Check the furnace
fuse, if OK possible break in the line
or bad furnace board. Shorting across
the two blue wires should make the furnace come on if voltage is present on one
of the 2 blue wires and IF the furnace control board is OK.
If you have a Heat
Pump and it gives heat when the controls are set for Cool, this is usually a
stuck reversing valve of the Freon system.
First verify that the reversing valve electrical coil is getting 120
volts from the control board -- if no 120 v, bad control board. If yes 120v, tap on the reversing valve while
the compressor is running to see if it will activate and start to cool. If the valve is permanently stuck compare
cost of repair to cost of a new air condition.
Run the air condition each month to keep the reversing valve lubricated.
IF YOU ARE NOT COMFORTABLE WITH ELECTRICAL TESTING, TAKE THE
COACH TO AN AUTHORIZED DOMETIC SERVICE CENTER